Home › Forum › Progea Community Forum › Movicon HMI solution for WinCE › Modbus RTU
Hello, I would like to communicate with a regulator connected in Modbus RTU. I can read the information but I can’t write a new information (example: setpoint change).
How can I do it? The doc gives me the address of the CHECKSUM.
It depends on how you have configured the communication task in the variable and whether the type of register you are exchanging allows writing.
Progea SrlVia D’Annunzio 295,I-41123 Modena (Italy)View on map
Italia: HQ +39 059 451060Internazionale: +41 91 9676610Germania: +49 7721 99 838 0USA: +1 888 305 2999